what is the synchronizing panel?
Synchronizing panel The name itself describes its role when you link with Power Source. Means – To compare, match, adjust with two or more power magnitude levels. The demand of synchronizing panels comes into action where power continuity is at a priority level. In Conclusion, Synchronising panels is the most important part for critical production industries in LT Panels
origin from the basic
First of all, I would like to introduce its back up a player called AMF(Auto Mains Failure) Panel on which the whole scenario depends. At every place where power continuity is the primary requirement, you have depended on alternate sources besides mains grid incomer. So you have to rely on captive power plants like Diesel/UPS/Batteries/Wind/Solar etc. no concern whether it is renewable or non-renewable sources of energy.
principle of operation
All Power sources connected to common busbars using motorized circuit breakers or Air circuit breakers. Whenever the main grid supply fails, Synchronizing relay comes into action and give control signal to alternate sources. So DG connected to common busbars. After that initial warmup, DG starts and allowed to rotate at full speed.
Firstly, all indoor panels have the protection of IP54 or better even more all outdoor panels have protected with IP65 or better. Secondly, all PCC Panels made by laser cutting CRCA sheet and powder coating with the 7-Tank process.
- Advanced as well as reliable control module
- Full range protection function, and alarm shutdown feature
- Synchronizing relays Woodward/Stucke/DEIF/Deepsea.
- Power Generation Continuity
- Protection class of IP52/IP55/IP65.
- Ratings upto 6000A.
- Generator and grid electricity Board feeder for AMF function.
- Both Active and reactive power load sharing and avoids overloading of either system.
Standards of Dg Synchronizing Panel
Synchronization Panel are designed as per IS standard IS 8623, IEC 60529. In addition, all switches and the circuit breakers, connectors conformed to IEC 60947, part I, II and III/ IS 60947 part I, II and III.
Synchronization panels mostly designed and used to synchronize power Sources like DG and Mains Synchronizing or Solar and Grid Synchronizing etc.